Dairy Establishment Inspection Manual – Chapter 14 - Aseptic Processing and Packaging Systems
1.14.03 Constant Level Tank (CLT)
This page is part of the Guidance Document Repository (GDR).
Looking for related documents?
Search for related documents in the Guidance Document Repository
The constant level tank (CLT) is a reservoir for supply, at atmospheric pressure, of raw product to the sterilizer to permit continuous operation of the aseptic processing and packaging system. The constant level tank is located at the start of the APPS system. The constant level tank controls the milk level and provides a uniform head pressure to the product leaving the tank.
1.14.03.01 General Conditions
The tank shall be constructed of stainless steel and be in good mechanical and sanitary condition. The tank's design features will be assessed under the subsequent tasks.
The tank shall be of such design and capacity that air shall not be drawn in the system with the product when operating at the maximum sealed capacity of the flow control device. The constant level tank shall therefore be fabricated so that the raw product will drain to the outlet before the outlet becomes uncovered. One method of complying with this requirement is to have the bottom of the tank pitched to the outlet at a minimum downward slope of at least 2% (0.2 cm per 10 cm) and the top of the outlet pipe lower than the lowest point in the tank (see Appendix 19 - 3).
The tank shall be fitted with a removable cover, or an inspection port with a removable cover, of suitable design to maintain atmospheric pressure and to minimize the risk of contamination. The cover shall be pitched to an outside edge to provide drainage. All openings in the cover shall be flanged upwards and covered. Pipelines entering through the cover (excluding directly clamped lines) shall be fitted with a sanitary umbrella deflector that overlaps the edges of the opening and is located as close to the tank cover as practical. The cover shall be used during processing.
1.14.03.04 Airspace and Overflow
Any product divert lines, recycle lines and water lines coming into the constant level tank (CLT) must be installed in a way that prevents the siphoning of raw milk or cleaning products into finished product or potable water lines (a cross connection). This is accomplished by having an overflow outlet at least twice the diameter of the largest inlet to the constant level tank, and ensuring that the divert, recycle, water lines terminate and break to atmosphere at least two times the diameter of the largest inlet above the maximum overflow point of the CLT
1.14.03.05 Level Control Device
This device is required to control the flow of milk to the constant level tank and therefore provide constant head pressure to the product leaving the tank.
The constant level tank shall be equipped with an automatic device of sanitary design and construction to control the raw product level.
- Date modified: